Gateways for BACnet Networks
Gateways for Modbus Networks
Gateways for LonWorks Networks
Gateways for SNMP Networks
Gateways for Proprietary Protocols
AddMe III Full Size Web Servers
AddMe Jr. Compact Web Servers
i.Board Economy Web Servers
BAS-700 Series Legacy Modular I/O for SNMP, Modbus TCP
Programmable I/O for BACnet
Programmable I/O for Modbus RTU
Remote Monitoring Devices
Remote Monitoring Subscriptions
> Babel Buster SPX-B BACnet IP to Modbus RTU and TCP Gateway
You are currently visiting our e-Commerce site. Full documentation, user guides, data sheets, videos,
and more as applicable by product, may be found at
Babel Buster SPX-B BACnet IP to Modbus Gateway is a BACnet IP client & server with a Modbus RTU master and slave, plus Modbus TCP client and server, for connecting Modbus devices to a BACnet IP network or vice versa.
Babel Buster SPX-B BACnet IP to Modbus RTU and TCP Gateway
Device Firmware Version
Standard BACnet IP to Modbus Gateway
SNMP Client/Server Included
Extended Memory Option
Extended Memory, 10X File Capacity [+$40.00]
Put me on the Waiting List
Add to Cart
Babel Buster SPX-B contains three different clients and three different servers. The SPX-B includes BACnet/IP client and server, Modbus TCP client and server (master and slave), and Modbus RTU master and slave.
The BACnet IP client allows BACnet IP devices to be accessible from Modbus TCP or RTU. You configure the device instance, object type and instance, and poll interval for reading or writing BACnet objects. The object data is stored in the IP/XM server for subsequent retrieval by any supported remote client (or master).
A large number of BACnet objects gives you flexibility in mapping Modbus registers to any combination of BACnet objects. Packed Modbus registers may be parsed to multiple BACnet objects when reading. Multiple BACnet objects may be packed into a single Modbus register when writing. All standard Modbus register types are supported.
SPX-B2 adds an SNMP client and server. The SNMP client allows SNMP devices to be accessible from BACnet IP or Modbus. You configure the SNMP agent's IP address, the OID of the MIB variable you wish to poll, and set a polling interval. The object data is stored in the SPX-B server for subsequent retrieval by any supported remote client.
Value objects will poll their assigned Modbus register at the interval you specify. The content of the Modbus register will be given as the Present Value of the BACnet object when read. The Modbus register is written each time the BACnet Value object is written. The Value object corresponds well with the Modbus Holding register.
Input objects will poll their assigned Modbus register at the interval you specify, and provide the Modbus data as the Present Value when read. Commandable Output objects are used to write Modbus registers, and will update the Modbus device each time BACnet is updated.
The same polling schemes that apply to Modbus also apply to remote BACnet IP slaves polled by the SPX-B's BACnet IP client, and apply to SNMP or WiFi sensor polling as applicable.
• Universal, fully configurable
• No extra software or drivers to buy
• Read/Write any standard Modbus register via BACnet
• Read/Write any standard BACnet object via Modbus
• Bidirectional communication between BACnet and Modbus
• Supports Modbus “coils”, input registers, holding registers
• Single or double Modbus registers
• Signed, unsigned, IEEE 754
• Modbus register mapping configured via web interface
• Modbus registers may be scaled (x10, x0.1, etc.)
• Modbus (master) polling interval configurable per point
• Commandable BACnet objects implement priority array
• Hardened EIA-485 transceiver for Modbus RTU
• 10/100BaseT Ethernet for BACnet IP and Modbus TCP
• Powered by 10-30VDC or 12-24VAC 50/60 Hz
• Power Consumption: 0.1A @ 24VDC
• Panel mount, 70mm H x 131mm W x 38mm D
• Pluggable screw terminal block for power & RTU network
• Operating temperature -40°C to +85°C
• Humidity 5% to 90%
• FCC Class A, CE Mark
AM3-SM AddMe III Modbus RTU 32-point I/O, Freely Programmable
AMJR-14-IP AddMe Jr. i.CanDoIt Web Server, 14-point I/O, Modbus, SNMP
Babel Buster BB2-3010 BACnet MS/TP to Modbus RTU Gateway
Babel Buster BB2-6010 Modbus to SNMP, Modbus RTU to TCP Gateway
Babel Buster BB2-7030 BACnet Gateway and Router
IB-100 i.Board i.CanDoIt Web Server, 10-point I/O, Modbus TCP, SNMP
IB-110 i.Board i.CanDoIt Web Server, 8-input with Modbus RTU, Modbus TCP, SNMP